I have a 560 humidifier with a model 883321B controller. The past 6 years we owned the house we never used the humidifier but now we are trying to use it. We recently had a evaporator coil and new thermostat installed and the installer ran new wiring for it. When I tried to run the humidifier, water continually runs weather the furnace is on or off and no matter what the humidistat is set to. There was no voltage at the solenoid valve when I checked.
Thank you for contacting us regarding your model 560 humidifier. When the unit is wired properly, the solenoid valve should only open when the furnace and HVAC blower is running. If there is no voltage at the solenoid and it is open, then the valve may be stuck open due to a build up of particles or sediment.
In order to send you to correct wiring diagram, we would need to know if you have a manual or automatic humidistat. Additionally, to better understand why your unit is not operating properly, you have the option to call our technical support department at 1-800-334-6011 to troubleshoot the unit with one of our technicians over the phone. The technician may be able to diagnose what the problem is and point you in the right direction regarding service or installation manuals.
Our tech support department is available Monday through Friday, 7 am to 5 pm CST.